HPO-9005 | Accessory: Room Sensor Adapter
OVERVIEW | Accessory: Room Sensor Adapter
The Room Sensor port in KMC Conquest controllers is designed to automatically connect and configure a digital STE-9000 Series NetSensor or an STE-6010, STE-6014, or STE-6017 analog (thermistor) sensor using a standard Ethernet patch cable.
The HPO-9005 room sensor adapter allows the use of other sensors and optional setpoint potentiometers to be used instead. This provides the means of reusing an existing suitable sensor and wiring in a retrofit or using a different kind of sensor (e.g., a flat plate sensor such as a STE-1430) for new installations.
The sensor must be a Type II or III, 10K ohm thermistor. The setpoint adjustment must be a 0-10K ohm potentiometer. The sensor or pot may have wire leads or (with user supplied wiring) screw terminals.
NOTE: Conquest controllers automatically configure Type II thermistors connected to the Room Sensor port. Type III thermistors require a quick configuration change using KMC Connect, KMC Converge, or TotalControl.