HPO-9005 | Accessory: Room Sensor Adapter for Conquest Controllers
OVERVIEW | Accessory: Room Sensor Adapter
The Room Sensor port in KMC Conquest controllers is designed to automatically connect and configure a digital STE-9000 series NetSensor or an STE-6010, STE-6014, or STE-6017 analog (thermistor) sensor using a standard Ethernet patch cable.
The HPO-9005 room sensor adapter allows the use of other sensors and optional setpoint potentiometers to be used instead. This provides the means of reusing an existing suitable sensor (e.g., STE-6011/6019) and wiring in a retrofit or using a different kind of sensor (e.g., a flat plate sensor such as a STE-1430) for new installations. (See the video introduction.)
The sensor must be a Type II or III, 10K ohm thermistor. The setpoint adjustment must be a 0-10K ohm potentiometer. The sensor or pot may have wire leads or (with user supplied wiring) screw terminals.
NOTE: Conquest controllers automatically configure Type II thermistors connected to the Room Sensor port. Type III thermistors require a quick configuration change using KMC Connect, KMC Converge, or TotalControl.
NOTE: The HPO-9005 is not compatible with STE-6012/6013/6020 sensors because of their required supply voltages.