STE-6010-10 | Sensor: Room Temp, Modular, Almond
OVERVIEW | Sensor: Room Temp, Modular, Almond
This compact, stylish, and economical room temperature sensor is designed for use with KMC digital controllers. It incorporates a 10,000 ohm (@ 77° F) thermistor for precise, stable temperature sensing and offers a variety of features. The durable, low-profile, thermostat-style cover is visually appealing. This sensor may be surface mounted on a hollow wall or (using an HMO-6036 universal backplate) to a 2 x 4 in. electrical box.
It has an RJ-45 modular jack for quick connections. For connecting to KMC Conquest BAC-59xx and BAC-9xxx controllers, use a standard Ethernet patch cable, such as a HSO-9001 (50 feet), HSO-9011 (50 feet, plenum-rated), or HSO-9012 (75 feet, plenum-rated) cable. For connecting to KMC KMDigital controllers and KMC legacy BAC-58×1 and BAC-7xxx BACnet controllers, use a (custom) KMD-5693 (25 feet), KMD-5694 (50 feet), or KMD-5695 (75 feet) cable.
A four-pin EIA-485 (formerly RS-485) data port on the cover’s underside provides an easy temporary computer connection to the network, using a:
- BAC-5051E router and HPO-5551 router technicians cable for BACnet networks.
- KMD-5576 USB-to-485 converter for KMDigital networks.
APPLICATION GUIDE, KMC CONQUEST CONTROLLER (Updated: 2023-06-09) [Rev. Q]APPLICATION GUIDE, Room Sensor and Thermostat Mounting and Maintenance (Updated: 2021-02-22) [Rev. F]Digital Designer's Guide (Collection of Misc. Application Notes) (Updated: 2010-04-16) [Rev. B]STE-6010/6011/6013/6015 Temp. Sensors Application Guide (Updated: 2020-12-01) [Rev. D]
- Data Sheets
STE-6010/6011/6013/6015 Room Temp. Sensors Installation Guide (Updated: 2020-11-25) [Rev. F]INSTALLATION GUIDE, Conquest BAC-5900 Series Controllers (Updated: 2022-12-22) [Rev. J]INSTALLATION GUIDE, Conquest BAC-9000 Series VAV Controller (Updated: 2022-12-22) [Rev. N]INSTALLATION GUIDE, Conquest BAC-9300 Series Controller (Updated: 2022-12-22) [Rev. J]
- Product Cross-References
- Selection Guides
- White Papers